Seek advice from that product’s set up sheet for directions. Twist and take away mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) gadgets that mechanically control lights via RF communication with a dimming or switching device. These Sensors detect the heat from individuals transferring within an space to determine when the house is occupied. The Sensors then transmit the appropriate commands to the associated dimming or switching system to turn the lights on or off robotically, providing both convenience and exceptional energy financial savings. Sensor does not perform satisfactorily from this location, it could also be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.3 and 1.4. 1.5 If the Sensor’s performance is passable, it ought to be completely attached to the ceiling tile, as described in section G. Everlasting Mounting. Momentary Strong Ceiling Mounting Use this process if the Sensor will be mounted on a stable, steady ceiling surface such as drywall, plaster, concrete, or wooden. Two 3M™ Command™ adhesive strips are supplied for briefly mounting and testing the Sensor on smooth, stable ceiling surfaces. These strips are designed for easy, damagefree elimination and are usually not reusable. These strips should not be used for permanently mounting the Sensor (see part G. Everlasting Mounting ). Fastidiously observe the removal directions below to make sure the ceiling is not broken throughout removing. Observe: Do not use the adhesive strips on ceiling tiles, as they'll possible cause damage to the tile upon removing. Simple-to-observe Instructions Set-Up In order for the Sensor to operate correctly, it must first be set up with a corresponding dimming or switching system. The process for organising a Sensor with a Maestro Wireless® (MRF2- solely) Dimmer or Electronic Switch is detailed below. P/N 041-172a 2.1 Peel the pink "Command Strips" liner off of one of the adhesive strips and apply the strip to the flat facet of the mounting bracket as proven within the diagram. Be aware: Do not cover the bracket’s screw holes as a result of they are going to be used to mark screw gap areas on the ceiling. Organising a Sensor with a Maestro Wireless Dimmer or Digital Switch Dimmer Key Features · Low Upkeep. 10-12 months battery life. Convenient low-battery indicator. · A number of Units. Up to 3 Sensors can work collectively to regulate lights for broader protection in large spaces. Every Sensor could also be added to as much as 10 receiving devices. Sensor Operation Occupancy Model - The Sensor will robotically flip the lights on when the house is occupied and routinely flip the lights off after the house is vacated. The Sensor will mechanically flip the lights off after the area is vacated. There is a built-in 15-second vacancy grace period that begins when the lights are robotically turned off, throughout which the lights will robotically flip again on in response to motion. This grace interval is supplied as a security and convenience feature in the event that the lights turn off whereas the room continues to be occupied, so that the user does not need to manually flip the lights again on. After 15 seconds, the grace period expires and the lights have to be manually turned on. This Sensor is part of a system and can't be used to control a load with out a appropriate dimming or switching gadget. Check with the instruction sheets of the receiving gadget(s) for set up data. The Sensor may be put in up to 60 ft (18.3 m) away from the associated dimming or switching system(s) if they are in direct line of sight. If there are walls or other barriers between the Sensor and receiving device(s), the Sensor must be situated within 30 ft (9.1 m). Warning: This product should not be used to regulate gear which may create hazardous conditions, resembling entrapment, if operated unintentionally. Sensor in a location where it has a broad view outside the supposed space. If this is unavoidable, the lens will be masked to block the view of undesired areas (check with section I. Lens Masking). This warranty is in lieu of all different express warranties, and the implied warranty of merchantability is proscribed to at least one yr from buy. This warranty does not cover the price of installation, elimination or reinstallation, or harm ensuing from misuse, abuse, or harm from improper wiring or installation. This guarantee does not cover incidental or consequential damages. LUTRON’S Legal responsibility ON ANY Declare FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Set up, Delivery, OR USE OF THE UNIT SHALL Never EXCEED THE PURCHASE Price OF THE UNIT. This warranty provides you specific legal rights, and you could produce other rights which differ from state to state. Some states do not allow the exclusion or limitation of incidental or consequential damages, or limitation on how long an implied warranty may last, so the above limitations could not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst logo are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American Nationwide Requirements Institute. IEC is a trademark of the Worldwide Electrotechnical Fee. Made and printed in the U.S.A. 25/09/09 P/N 041-172 Rev. A 8 ft (2.4 m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.Four m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) 16 ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.Eight m) Temporary Mounting Strategies 1.1 1.2 Insert the ceiling tile mounting wire by means of the two smaller holes in the mounting bracket and replace the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by way of the tile, ensuring the Sensor is flush to the tile. Notice: Do not twist wire legs together. 1.2 After the Sensor has been briefly mounted, go away the Sensor in place on the tile and both take the tile down or take away an adjoining tile to gain access to the legs of the mounting wire on the back of the tile. Low Exercise: That is essentially the most sensitive setting and can detect very slight motions. That is the recommended setting, as it will work nicely for nearly all functions. It is ideal for areas the place occupants will often be seated for long durations of time. Twist the wire legs collectively tightly so the mounting bracket stays snug against the tile. This setting is slightly less sensitive than the Low Activity setting and can be used for areas that experience regular exercise. That is the least delicate setting and can be utilized for areas that can typically solely experience massive motions, such as foot visitors. The Low Activity setting is the default and can carry out best for most applications. Hardly ever, if the Sensor is placed close to exterior noise sources comparable to heating vents, air conditioning vents, or gentle bulbs, it could flip the lights on without occupancy or keep the lights on too lengthy after vacancy. If this occurs, changing the sensitivity to Medium Exercise or Excessive Exercise ought to resolve the problem. Replace the tile. Everlasting Stable Ceiling Mounting 2.1 2.2 2.Three Superior Set-Up Operation The advanced set-up is accessed through the use of the buttons on the again of the Sensor. Drill two 3/sixteen in (4.6 mm) pilot holes for the offered screw anchors. Press the anchors into the holes and faucet flush with a hammer. To show the present setting, press and launch the desired button. An LED will illuminate briefly, indicating the current setting. Place the flat facet of the mounting bracket against the ceiling and install the 2 offered screws utilizing a hand screwdriver. To adjust a setting, press and hold the specified button until the LED corresponding to the current setting begins flashing quickly, indicating the setting can now be adjusted. Every subsequent button press of lower than 2 seconds will increment the mode to the subsequent obtainable setting. Pressing any of the opposite buttons will haven't any impact. To save lots of the chosen setting, press and hold the button until the LED turns on stable, indicating the saved setting. Through the adjustment process, if there isn't a activity for 30 seconds, the LEDs will flip off and no settings will be saved. Note: Do not over-tighten. 2.Four Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise path till the Sensor locks into place. To remove the bracket from the ceiling, grasp the elimination tab on the adhesive strip and pull the tab VERY SLOWLY straight across the ceiling, stretching the strip till the bracket releases from the ceiling. Discard the strip. By no means pull the strip at an angle, as it could break or harm the ceiling surface. Word: Don't pull at an angle. Lens Masking (Optional) At any time when attainable, the Sensor should be put in in a location the place it can't simply see into areas outside the supposed area, equivalent to hallways or adjacent rooms. If this case cannot be avoided, portions of the lens could also be masked with the supplied labels to dam the Sensor’s view of the undesired areas. It is suggested to remove the Sensor from the mounting bracket earlier than making use of Advanced Set-Up (Non-compulsory) the masking labels. The Sensor options a number of superior set-up modes. For nearly all of installations, the default settings will provide the very best efficiency and also you is not going to must make the most of the superior set-up. The Occupancy version of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Only model has only two modes (Auto-On not available). The default settings are listed under. The Sensor will be screwed onto the mounting bracket in several completely different orientations. Be certain to note the Sensor’s orientation earlier than taking it down and substitute the Sensor in the same orientation to ensure the meant area gets blocked. Outer lens sections correspond to the detection regions furthest away from the Sensor, whereas inner sections correspond to areas closer to the Sensor. Watch out when applying the labels to avoid creating gaps between adjoining masked sections. The Sensor might detect movement by way of inadvertent gaps. Always (Occupancy version only) Timeout 30 min 15 min 5 min Auto-On Always Low light Disable Activity Timeout 30 min 15 min 5 min Advanced Set-Up Modes Auto-On All the time Low gentle Disable Activity Exercise: Low Activity Lens sections shown in white are masked with labels Timeout The Sensor will flip the lights off if no motion happens during the timeout interval. There are three available timeout settings: 5, 15, and half-hour. Lens Mask Lens sections shown in grey haven't been masked Auto-On The automated-on performance of the Sensor could be adjusted to manage how the lights reply upon preliminary occupancy. There are three obtainable settings: At all times, Low mild, and Disable. Always: The lights will always turn on. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the entrance of the gadget. The lens will glow briefly, indicating the test mode has been entered. Note: There is a warm-up period of roughly 40 seconds after the batteries are put in earlier than the check mode could be activated. If the button is pressed throughout this time, the lens will flash repeatedly till the heat-up interval is full, after which the check mode might be automatically entered. Affirm the coverage space by strolling by way of the house and observing the lens. The lens will glow stable each time motion is detected. If the lens stays off during movement, the Sensor can not detect motion at that location. Press and launch the "Test: Sensor" button again to exit the take a look at mode. If the button is just not pressed, the test mode will mechanically day out quarter-hour after being enabled, or 5 minutes after the last detected movement if the room is vacated. If the Sensor has significant bother detecting motion through the test, it must be moved to a different location and retested. If the Sensor nonetheless has poor detection from the brand new location, seek advice from the Troubleshooting part. Momentary Drop Ceiling Mounting Use this process if the Sensor can be mounted on a ceiling tile. The ceiling tile mounting wire is offered for each temporary and everlasting mounting of the Sensor to drop ceilings composed of multiple tiles. It's designed to allow non permanent mounting, testing, and repositioning (if vital) of the Sensor with out damaging a ceiling tile. Once the Sensor’s final position has been chosen, the mounting wire may be twisted to lock the Sensor in place completely. If the Sensor protection and wireless communication exams have been successfully completed, use the mounting bracket as a template to mark the screw hole locations with a pencil. Notice: Pull very slowly. Max. Room Dimensions Radius of Coverage for Complete Coverage at Flooring If you are uncertain about correctly positioning the Sensor, the next temporary mounting and testing procedures are really helpful to verify correct efficiency earlier than permanently installing the Sensor. Sensor’s detection range relies on the ceiling peak, as shown within the desk below. Discover: Don't disassemble, crush, puncture, or incinerate the batteries. Do not dispose of batteries in normal household waste. Please recycle, take to a proper battery disposal facility, or contact your local waste disposal supplier concerning local restrictions on the disposal or recycling of batteries. O NOT mount the Sensor inside four ft (1.2 m) of HVAC vents or mild bulbs installed below the ceiling line. Warmer rooms could cut back the Sensor’s potential to detect occupants. Use solely excessive-quality lithium batteries, size CR123, 3 V (ANSI-5018LC, IEC-CR17345). Don't use rechargeable batteries. Utilizing improperly rated batteries could injury the Sensor. For questions concerning the installation or operation of this product, call the Lutron Technical Support Heart. Please present exact model number when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Mild Degree (occupancy model, dimming gadgets only) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach route till the Sensor locks into place. Sensor coverage and wireless communication assessments as described in 2.6 Carry out sections E. Testing Sensor Coverage and F. Testing Wireless Communication. The Sensor ought to be put in in a location where it has a superb view of all components of the room. The Sensor requires line of sight to operate correctly. If you cannot see the Sensor, it can not see you. The Sensor can not see by glass objects similar to patio or shower doorways. The vary and performance of the RF system is extremely dependent on a variety of complex elements reminiscent of: · Distance between system elements · Geometry of the constructing structure · Construction of walls separating system elements · Electrical tools positioned close to system components Technical Assistance 2.2 Identify a location on the ceiling where the Sensor will have a superb view of the room. 2.3 Take away the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use solely. Don't install on ceilings larger than 12 ft (3.7 m) or non-ceiling surfaces. Doing so might considerably inhibit the Sensor’s efficiency. 4. Don't paint Sensor. · · · · The "Lights On" and "Lights Off" buttons should now swap the lights within the room on and off, respectively, when pressed. Repeat the above procedure to set up the Sensor with any additional gadgets. The Sensor is intended for indoor use only. Operate between 32 °F and 104 °F (zero °C and 40 °C). 1.1 several seconds. Sensor that has been arrange. After roughly 6 seconds, the lens will flash quickly several instances, indicating the light level has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy mild degree. 2. Clear Sensor with a gentle damp cloth solely. Do not use any chemical cleaners. Note: This equipment has been tested and found to comply with the limits for a category B digital system, pursuant to half 15 of the FCC rules. These limits are designed to offer cheap protection in opposition to harmful interference in a residential installation. This gear generates, makes use of and might radiate radio frequency power and, if not put in and utilized in accordance with the directions, might cause harmful interference to radio and tv reception, which will be decided by turning the gear off and on. The person is inspired to try to right the interference by a number of of the following measures: Reorient or relocate the receiving antenna. Enhance the separation between the tools and receiver. Connect the tools into an outlet on a circuit completely different from that to which the receiver is connected. Consult the vendor or an experienced radio/Television technician for assist. Warning: Adjustments or modifications not expressly permitted by Lutron Electronics Co. could void the user’s authority to operate this tools. This machine complies with Half 15 of the FCC guidelines. This gadget must accept any interference obtained, including interference that may trigger undesired operation. Switch 2.1 Set the Dimmer to the specified mild degree for coming into the room. 2.2 Save holding the "Lights On" button on the entrance of a Note: For both Sensor version, the lights may also be manually turned off at any time by using the dimming or switching gadget straight. Vital Notes or Add the Sensor to the Dimmer or Switch by pressing and holding the "Lights Off" button on the entrance of the Sensor for roughly 6 seconds till the lens flashes briefly. The lights in the room will also flash 3 occasions, indicating the Sensor has been successfully added. The Dimmer or Swap will exit set-up mode robotically. The sensitivity of the Sensor could be adjusted primarily based on the expected stage of activity within the room. There are three accessible exercise settings: Low Activity, Medium Activity, and Excessive Activity. Everlasting Drop Ceiling Mounting Word: Leave the removal tab exposed previous the sting of the bracket so it may be accessed for removal later. 6 seconds until all LEDs on the machine begin flashing. Launch the faucet button. Sensor is detecting motion in areas that aren't fascinating, corresponding to hallways or adjoining rooms, confer with part I. Lens Masking. If Sensor detection is satisfactory throughout this test, carry out the wireless communication test as described in section F. Testing Wireless Communication. Testing Wireless Communication This check ought to be carried out to verify that the Sensor has been accurately arrange with the corresponding dimming or switching gadget and that there is proper wireless communication from the chosen Sensor location. If the lights within the room should not on, turn them ON manually on the dimming or switching gadget. Press and release the "Lights Off" button on the front of the Sensor. The lights should turn OFF. Press and launch the "Lights On" button on the front of the Sensor. The lights should turn on. If the lights do not reply accurately, check with the Troubleshooting section. Low light: The lights will solely turn on routinely upon entry if there shouldn't be already sufficient ambient mild within the room. Hallway falls within Sensor’s protection space. Disable: This setting converts the Sensor to vacancy mode. The lights is not going to automatically activate but will nonetheless routinely turn off after vacancy. The lights should be manually turned on by utilizing the related dimming or switching system. Observe: The 15-second vacancy grace period is energetic in this mode. Refer to the Sensor Operation part at first of this doc for extra particulars. Troubleshooting Symptom Attainable Causes Resolution Lights do not turn on when house is occupied. Sensor is not appropriately added to dimming / switching machine(s). Sensor’s Auto-On setting is set to "Low light" or "Disable". The lights had been recently turned off manually and the timeout has not yet expired. Sensor doesn't have full view of room. Sensor is exterior wireless range of dimming/switching gadget. Consult with part B. Set-Up. Discuss with section H. Advanced Set-Up. Dimming/switching gadget has been improperly wired. Mild bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is too short for this software. Sensor does not have full view of room. Lens mask is improperly applied. Sensor’s sensitivity is simply too low. Sensor’s timeout has not but expired. An exterior noise source resembling an HVAC vent is interfering. Discuss with section A. Pre-Installation. Conduct of lights doesn't match Sensor settings. Sensor coverage extends past room perimeter. The meant setting was not saved. A number of Sensors are added to a dimming/switching system and their settings do not match. Seek advice from section A. Pre-Installation. Check with part C. Sensor Placement or I. Lens Masking. Consult with part H. Superior Set-Up. Refer to part H. Advanced Set-Up. Sensor lens doesn't glow in response to motion throughout Sensor protection testing. Sensor can not see motion resulting from obstruction. Room is too massive or oddly formed. Transfer Sensor to another location. Discuss with section C. Sensor Placement. A number of Sensors may be needed for full room protection. Attempt transferring Sensor to a brand new location or reducing sensitivity. Confer with part C. Sensor Placement or H. Superior Set-Up. Lights flip OFF while space is occupied. Lights keep ON after space is vacated. Lens doesn't stop glowing throughout Sensor coverage testing even when there isn't a motion. Lights do not reply correctly during wireless communication testing. Sensor lens flashes and lights don't activate when area is occupied. Battery has been put in incorrectly. An external noise source reminiscent of an HVAC vent is interfering. Seek advice from part C. Sensor Placement. Confer with section C. Sensor Placement or F. Testing Wireless Communication. Seek advice from section H. Superior Set-Up. Confer with part C. Sensor Placement. Check with section I. Lens Masking. Refer to part H. Advanced Set-Up. Check with part H. Superior Set-Up. Strive transferring Sensor to a new location or reducing sensitivity. Check with part C. Sensor Placement or H. Superior Set-Up. Sensor isn't appropriately added to dimming / switching machine. Sensor is exterior wireless range of dimming/switching gadget. Refer to part B. Set-Up. Transfer Sensor closer to dimming/switching machine and retry take a look at. Discuss with section F. Testing Wireless Communication. Battery has been put in incorrectly. Dimming/switching device has been improperly wired. Mild bulb(s) burned out. Breaker is off or tripped. Battery is low. Refer to section A. Pre-Set up. Take away sensor from take a look at mode. Refer to section E. Testing Sensor Protection.
Stop by my site - od.lk